ARSENIC AND IRON
Groundwater is the main source of water
supply in Bangladesh. Groundwater
abstracted from tubewells was
considered to be the best option for
water supply in rural and peri-urban
areas. Unfortunately, arsenic in excess
of the acceptable limit has been found
in tubewell water in many parts of the
world and particularly in Bangladesh.
Alternative options for arsenic-safe
water are urgently needed to mitigate
arsenic toxicity and protect public
health and there has been considerable
research into a range of technologies.
Some of the common arsenic mitigation
Co-precipitation of arsenic and iron
Adsorption of arsenic onto coagulated
Adsorption onto sorptive media
Filtering by special membrane
One low-cost option based on the co-
precipitation principle that is showing
promises is the arsenic and iron removal
plant (AIRP) that has been tested in
Bangladesh. This approach to arsenic
mitigation is described in this Technical
How does the AIRP system work?
Figure 1: AIRP Design.
The basic structure of the 4 chamber plant is shown in Figure 1. Water contaminated with
arsenic and iron from the source tubewell is introduced to chamber C1. The water spreads
through the perforations of the inlet pipe. This action aerates the water. In the aeration
process, oxygen from the air reacts with iron and arsenic in the water. This transforms the
soluble arsenic and iron into insoluble compounds. The insoluble arsenic and iron
Practical Action, The Schumacher Centre, Bourton on Dunsmore, Rugby, Warwickshire, CV23 9QZ, UK
T +44 (0)1926 634400 | F +44 (0)1926 634401 | E email@example.com | W www.practicalaction.org
Practical Action is a registered charity and company limited by guarantee.
Company Reg. No. 871954, England | Reg. Charity No.247257 | VAT No. 880 9924 76 |
Patron HRH The Prince of Wales, KG, KT, GCB